|Water is not getting cold.||Standard water dispenser (non-chilled)
Water chiller is not operating properly.
|Standard unit only supplies ambient temperature water.
Refer to water chiller manual.
|Water runs continuously from water dispenser.||Sensor is defective or dirty.||Clean or replace sensor.|
|Solenoid or solenoid diaphragm is defective.||Replace solenoid water valve.
Note: To verify faulty solenoid, disconnect the power while water is running. If water flow does not stop immediately then replace the solenoid.
|Low water flow.||Supply water pressure is less than required.||Water pressure must be between 40 and 105 psi.|
|Filter is plugged.||Replace filter.|
|Solenoid water valve not opening fully.||Restore power to the unit.|
|No water flow.||No electrical power.||Restore power to the unit.|
|Water shut‑off valve(s) closed.||Open all shut‑off valves (one is located inside the filter box if installed and another may be at the water source).|
|Bottle sensor is not operating properly.||Sensor is malfunctioning and must be replaced.|
|Blinking red light.||No filter.||Replace filter.|
|Filter incorrectly installed.||Check filter is completely installed.|
|Blinking red and blue light.||Filter wire disconnected.||
Check filter cable connections.